Fukushima Nuclear Accident Update Log
Updates of 21 April 2011
- Story Resources
- In Focus: Fukushima Nuclear Accident
- Fukushima Nuclear Accident: Information Sheet
- Criteria for Use in Preparedness and Response for a Nuclear or Radiological Emergency
- International Nuclear and Radiological Event Scale (INES)
- IAEA Incident and Emergency Centre (IEC)
- International Seismic Safety Centre (ISSC)
- Response Assistance Network (RANET)
- Japan Nuclear and Industrial Safety Agency (NISA)
IAEA Briefing on Fukushima Nuclear Accident (21 April 2011, 16:25 UTC)
→ Summary of Reactor Status
(Note: Unless there are significant developments, no further written brief will be issued until Tuesday 26 April.)
On Thursday, 21 April 2011, the IAEA provided the following information on the current status of nuclear safety in Japan:
1. Current Situation
Overall, the situation at the Fukushima Daiichi nuclear power plant remains very serious, but there are signs of recovery in some functions, such as electrical power and instrumentation.
At a press conference held at 11:00 (Japan local time) on 21 April, the chief cabinet secretary, Mr. Edano, announced the establishment of a no entry zone around Fukushima Daiichi nuclear power plant, as well as basic policies concerning temporary re-entry. As of midnight (Japan local time) on 22 April 2011, the area within 20 km of Fukushima Daiichi nuclear power plant is announced as a no entry zone.
Chief cabinet secretary, Mr. Edano, also announced a re-designation of the evacuation zone around Fukushima Daini nuclear power plant. He announced that "the size of the evacuation zone around the station would be reduced from 10 km to 8 km," and that "the order to evacuate based on the incident at Fukushima Daini nuclear power station would be lifted from areas farther than 8 km around the station."
Changes to Fukushima Daiichi Nuclear Power Plant Status
The IAEA receives information from a variety of official Japanese sources through the Japanese national competent authority, the Nuclear and Industrial Safety Agency.
Management of On-site Contaminated Water
Injection of approximately 17 000 L of coagulant (liquid glass) to the power cable trench of Unit 2 was carried out on 18 April and injection of approximately 7 000 L of liquid glass on 19 April. The transfer of stagnant water from the Unit 2 turbine building to radioactive waste treatment facilities commenced on 19 April.
The stagnant water (around 100 m3) in the basement of the turbine building of Unit 6 was transferred to the condenser on 19 April.
Work to strengthen the electrical power system between Units 1 - 2 and Units 3 - 4 by establishing multiple power lines was completed on 19 April.
White "smoke" continues to be emitted from Units 2, 3 and 4.
In Unit 1 fresh water is being continuously injected into the reactor pressure vessel through the feedwater line at an indicated flow rate of 6 m3/h using a temporary electric pump with off-site power.
In Unit 2 and Unit 3 fresh water is being continuously injected into the reactor pressure vessel through the fire extinguisher line at an indicated rate of 7 m3/h using temporary electric pumps with off-site power.
In Unit 4 40 tonnes of fresh water was sprayed over the spent fuel pool on 19 April using a concrete pump truck.
Nitrogen gas is being injected into the containment vessel in Unit 1 to reduce the possibility of hydrogen combustion in the containment vessel. The pressure in the containment vessel has stabilized. The pressure in the reactor pressure vessel is increasing.
The reactor pressure vessel temperatures in Unit 1 remain above cold shutdown conditions. The indicated temperature at the feedwater nozzle of the reactor pressure vessel is 154 °C and at the bottom of reactor pressure vessel is 113 °C.
The reactor pressure vessel temperatures in Unit 2 remain above cold shutdown conditions. The indicated temperature at the feed water nozzle of the reactor pressure vessel is 135 °C. The reactor pressure vessel and the dry well remain at atmospheric pressure. Fresh water injection (approximately 47 tonnes) to the spent fuel pool via the spent fuel pool cooling line was carried out on 19 April.
The temperature at the bottom of the reactor pressure vessel in Unit 3 remains above cold shutdown conditions. The indicated temperature at the feed water nozzle of the reactor pressure vessel is 100 °C and at the bottom of the reactor pressure vessel is 108 °C. The reactor pressure vessel and the dry well remain at atmospheric pressure.
There has been no change in the status in Unit 6 or in the common spent fuel storage facility.
2. Radiation Monitoring
On 20 April, deposition of I-131 was detected in 8 prefectures, ranging from 2.4 to 80 Bq/m2. Deposition of Cs-137 was detected in seven prefectures, the values reported ranging from 2.6 to 87 Bq/m2.
Gamma dose rates are measured daily in all 47 prefectures. For Fukushima on 20 April a gamma dose rate of 1.9 µSv/h was reported, and for Ibaraki prefecture a gamma dose rate of 0.12 µSv/h was reported. In all other prefectures, reported gamma dose rates were below 0.1 µSv/h.
Dose rates are also reported specifically for the eastern part of Fukushima prefecture, for distances beyond 30 km from Fukushima Daiichi. On 19 April the values in this area ranged from 0.1 to 22 µSv/h.
In cooperation with local universities, the Japanese Ministry of Education, Culture, Sports, Science and Technology (MEXT) has set up an additional monitoring programme. For 20 April, measurements of gamma dose rates were reported for 54 cities in 40 prefectures. In Fukushima City a value of 0.42 µSv/h was reported. For nine cities, gamma dose rates between 0.13 and 0.17 µSv/h were reported. For all other cities reported gamma dose rates were below 0.1 µSv/h.
I-131 or Cs-137 is detectable in drinking water, but at levels below 1 Bq/L and in only a few prefectures. As of 20 April, one restriction on drinking water for infants relating to I-131 (100 Bq/L) remains in place for a small scale water supply in a village of the Fukushima prefecture.
Food monitoring data reported by the Japanese Ministry of Health, Labour and Welfare on 20 April covered a total of 103 samples. These samples were taken on 3, 14, 15, 18, 19 and 20 April from nine prefectures (Chiba, Fukushima, Gunma, Ibaraki, Kanagawa, Niigata, Tochigi, Tokyo and Yamagata).
Analytical results for 99 samples of various vegetables, shiitake mushrooms, fruit (strawberries), fish, seafood and unprocessed raw milk indicated that I-131, Cs-134 and Cs-137 were either not detected or had levels below the regulation values set by the Japanese authorities. Four samples of leafy vegetables (Japanese parsley, komatsuna, shinobuhuyuna and spinach) taken on 18 April from Fukushima prefecture had levels above the regulation values set by the Japanese authorities for radioactive caesium.
On 20 April, restrictions were placed on the distribution and consumption of the young of a specific sea fish (sand lance) from the coastal region of Fukushima prefecture. As has been reported previously, sand lance is the only seafood that has been found with I-131, Cs-134 or Cs-137 levels above the regulation values set by the Japanese authorities.
3. Marine Monitoring
TEPCO Seawater Monitoring Programme
TEPCO is conducting a programme for seawater monitoring (by surface sampling) at a number of near-shore and off-shore monitoring locations. Following a directive from NISA, on 16 April TEPCO announced that it will increase the number of sea sampling points from ten to 16. A further four points are to be added at 3 km from the coast and two points are to be added at 8 km from the coast. The new sampling sites are indicated on Map 1: TEPCO Seawater Sampling Locations, on which new points are indicated with green bullets.
On some days, two samples were collected at the same sampling point, a few hours apart, and analysed separately.
Until 3 April a generally decreasing trend in radioactivity was observed at the sampling points TEPCO 1 to TEPCO 4. After the discharge of contaminated water from the plant on 4 April, a temporary increase in radioactivity in sea water was reported. Since 5 April a general downward trend in the concentration of radionuclides in sea water for all TEPCO sampling points has been observed.
On 21 April new data for TEPCO sampling points were reported. For TEPCO 1 - 4 (sampling date 19 April) the values for both I-131 and Cs-137 were below 0.5 kBq/L. For TEPCO 5 - 10 (sampling date 18 April) the values for both I-131 and Cs-137 were below 0.3 kBq/L.
For the six new stations at 3 km off-shore and 8 km off-shore (green bullets in Map 1; sampling date 18 April), I-131 and Cs-137 were not detectable at the two stations 3 km off-shore; for all the other stations the level of I-131 was below 0.3 kBq/L and that of Cs-137 was below 0.4 kBq/L.
MEXT Off-shore Seawater Monitoring Programme
On 21 April new data were reported (sampling date 19 April)for the MEXT 2, 4, 6, 8, 10 and B off-shore seawater sampling locations shown in Map 2: MEXT Seawater Sampling Locations. I-131 was detected only at the location MEXT 6 and the level was below 20Bq/L. Cs-137 was detected at locations MEXT 6 and 8 at a level of below 30 Bq/L.
4. IAEA Activities
Georgia and Iceland have also provided monitoring data, in addition to the States that have been mentioned in previous briefs.
On 18 April the IAEA monitoring team finished its radiological monitoring campaign and the team returned to Vienna on 20 April.